BYA-FiR I Single Core (Cu/Mica Tape/PVC-FR)
*REACH I RoHS I CE
During fire, electric circuits and the associated lighting may be damaged. Power and data communications may be suspended. Human safety may depend on continued operation of lighting, elevators and escalators, fire fighting water pumps, fire alarm and ventilation fans.
Fire barrier: Mica tape (Synthetic or Glass)
Insulation : Flame Retardant (FR) PVC, Tl1-FR to BS 7655
cable) exceeds IEC 60331 – 3 hours at 750 °C – when the test temperature was increased to 950°C,
equivalent to BS 6387 category C.
Fire resistance test – IEC 60331-21, BS 6387
Flame retardant test – IEC 60332-1-2
Uo/U (UM) : 450/750V
Test Voltage : 1.5-2.5 kV
– 20°C to +70°C
Max Short Circuit : 750°C